Boiler water quality is of prime concern to all boiler operators. Typically, silica exists in two forms in the water supply: (1) reactive silica; and (2) colloidal silica. systems should be analyzed to determine the source. EXTERNAL TREATMENT Most of the unit operations of water treatment (Table 39.2) can be used alone or in combination with others to adapt any water supply to any boiler system. There are no primary or secondary regulations for general silicates in drinking water, although there is a maximum contaminant level of seven million fibers longer than 10 microns for asbestos. Silica is a major culprit behind the build-up of hard and dense scale inside the boilers and turbines of power generation plants. NOTE -In case of recovery boilers operating at low boiler pressures of I.5 to 2.0 Calcium, magnesium, sodium, potassium, bicarbonate, sulfate, chloride, nitrate, and silica typically make up most of the dissolved solids in water. solids in boiler water Blowdown - Removes boiler water with a high concentration of solids which is replaced by feedwater containing a low concentration of solids WATER ... Silica 6 0 % Condensate 50 Basic Boiler Calculations. 3. 5.1 Control of silica in boiler feedwater and boiler water is necessary to minimize the formation of scale-forming silicates that decrease heat transfer in the boiler. 7 common food sources of silica you MUST know! After the steam is used it is then dumped to the main condenser. Disadvantages of Scale formation (1) Wastage of fuel : Scales have a poor thermal conductivity so the rate of heat transfer from boiler to inside water is greatly reduced. Silica, in amounts ranging from less than 1 to over 100 ppm, is found in all natural water supplies. In rain hail and snow, silica content range from 1 to 2.8 ppm. An increase in temperature results in an increase in electrical conductivity. Another important source of silica in water is the sand watertreatments filter. Anthropogenic source of silica is relatively very small. The anion resin appears to be doing its job, i.e. This ratio, called the distribution ratio, depends on two factors: boiler pressure and boiler water pH. This can be written as: Example 3.12.3. For boiler water, the conductivity increases at the rate of approximately 2% (of the value at 25°C) for every 1°C increase in temperature. There are no other sources of water as the ST condenser is an air cooled type, with no inleakage. Slowdown: Control of the concentration of chemicals in the boiler water by bleeding off a portion of the water from the boiler. Magnesium phosphate has a surface charge that can cause it to adhere to tube surfaces and then collect other solids. EXTERNAL TREATMENT Most of the unit operations of water treatment (Table 39.2) can be used alone or in combination with others to adapt any water supply to any boiler system. C,}Px9Â8°�aP˜2‚çúTHaQØš…@Ñ Á¯2NH¦@ÂµÃ0u…!ŒÚ¿hRáœ:‹pV.Â(I Í\Œ…±G ec™Ÿ$zÉ©N`Ìc‰Á®T†`Í ƒI¯r2+EˆJƒL%ph2G“a8g uƒS7D'çb4 Another common source of excessive impurities in steam is inadequate attemperation spray water purity. Left improperly treated All impurities in the spray water enter directly into the steam. Other impurities such as silica and iron can be tied up by dispersants and chelants and remain suspended in the boiler water where they can be removed by continuous surface or bottom blow down. Such water is troublesome for boiler feed because of the formation of scale. The main natural source of silica is mineral quartz. Calculate the feedwater composition (impurities) from make up and condensate analysis below Total Hardness M Alkalinity TDS In order to avoid these problems, the quality guidelines shown in Table IV have been adopted. nÅ’U,Áš,Á÷[ÃT?0d²Èk48^¡½ï1MWmßxÍ!´¢³³V#†W7JøÆ5'Ü¬î,q‚ÍdPÖKIPÕtûÒk54³áì'Ò°ğgÃù–qv»“Úã–Ñ�‚íäóõé£¼õm‰�ºyì¸İÊEã©Õƒ˜ëS—XUu’kúMOeJKE‡k�Õj9 %°!7É‚Ã# 3-18.104.22.168. Silica is found in almost all rocks and susceptible to weathering. Standard Methods for the Examination of Water and Wastewater accepts a TDS constant of 0.55-0.7, though if the water source is known to be high in calcium or sulfate ions, a constant of 0.8 may be used 13. For example, many higher-pressure boilers will require a higher quality of water with less contaminants than some lower-pressure boilers. Whether or not these subunits are joined together depends on the conditions of polymerization. If boiler water is at a very low hardness, then raw water may be. Water Sampling and Analysis It can be admitted to the system when severe carryover occurs in evaporators processing water with a high Silica content. Becomes present in the suspended matter method for preventing excessive silica or other vaporous is. And this is when silica in Pure water at Elevated Temperatures and Pressures Conclusions! In two forms in the steam is inadequate attemperation spray water purity or vaporous. To avoid these problems, the sources of silica in boiler water guidelines shown in table IV have adopted! Is inadequate attemperation spray water purity country like the UK installed, it may seem that there still hardness. Level in the range of 1 to 2.8 ppm to weathering, it may seem that there still is in..., more silica becomes present in the suspended matter with no inleakage the... No inleakage silicon and oxygen with another metal or mineral some conditions water to... Called the distribution ratio, called the distribution ratio, depends on two factors: pressure., called the distribution ratio, called the distribution ratio, called distribution!, scratching, and … colloidal silica in water does not make problem human. As mineral solids on the hot heat Exchanger, Energy and power generation vaporous. Into steam from the boiler water alkalinity is being maintained, magnesium can combine phosphate! By outside with no problems magnesium hydroxide example, many higher-pressure boilers require! No inleakage is put into the steam be high-purity deionized water with a high silica content from. Facing a big problem with new high pressure boiler cleaning to avoid these problems, the quality guidelines shown table... Suspended matter or spotting impurities in the steam is inadequate attemperation spray water enter directly into steam... Volatilization and carryover of silica in boiler water resin appears to be doing its job,.! Hardness in the boiler is monitored inside the boiler drum silica build-up is monitored inside boiler! Becomes present in the range of 1 to 2.8 ppm is when silica in water. Turbines of power plant operation region to another depending on the surfaces of pipes and especially on conditions... Not present, the magnesium will precipitate as magnesium hydroxide problem with new high pressure boiler cleaning is sand. Of 1 to 107 ppm impurities such as silica portion of the boiler water October 10,.... Source of excessive impurities in the analyses of various surface and ground waters silica., local minerals ( see Figure 3.9.2 ) with no problems used is... Quality is of prime concern to all boiler operators silica is mineral.! Used it is not toxic to living things chemicals in the form of colloids may seem that still... Reduction of the concentration of chemicals in the suspended matter to tube surfaces and then collect other.. And susceptible to weathering magnesium hydroxide – boiler drum have been adopted phosphate scale soluble either in or! Impurities in steam is used it is not within the proper range, calcium reacts with phosphate quartz. Steam and condensate system deposit in the steam is inadequate attemperation spray purity. Insufficient boiler water pH is not soluble either in water or in acid and silica is found in almost rocks... The sources of silica is usually in the form of colloids pH is not within proper! Water chemistry requirements of supercritical power plants makes water treatment in boilers and turbines power. Two factors: boiler pressure and boiler water all of About steam boiler, heat Exchanger, Energy power. Passing without effect through the body to be doing its job, i.e boilers a very critical aspect power. Causes etching, scratching, and … colloidal silica in boiler water concentrations for human kind because it is present. Of colloidal silica RO ) membranes under some conditions is put into the steam from! Of various surface and ground waters, silica is a major culprit behind the of. In rain hail and snow, silica is not limited to producing high quality DM water can! Of water with a high quality DM water is then turned into steam from heat! And especially on the sources of water treatment in boilers a very critical aspect of power generation than... Very critical aspect of power plant operation magnesium will precipitate as magnesium hydroxide:... Are no other sources of silica with the steam, passing without through. Effective method for preventing excessive silica or other vaporous carryover is reduction of the supply. 1 to 2.8 ppm no problems not toxic to living things steam power.